Voltage regulation problems account for more than 90% of the power
quality problems seen at most sites. The MODERN Voltage Stabilizers
provide protection against mains power sags, surges and brownouts.
It is ideal for geographical regions that are subject to
inconsistencies in the mains supply, such as Africa, Asia and
certain parts of Europe.
Each stabilizer/regulator has a wide input voltage tolerance, and
has been designed to provide the ultimate reliability in hostile
environments, where the quality of the mains supply cannot be
We are Manufacturer which specialized in Servo Voltage Stabilizer,
Uninterruptible Power Supply (UPS), Active Power Filter, etc for
over 40 years. And we are vendor of Mitsubishi Elevator in East
Africa, GE, Emerson.
BROADCAST: Regulation for broadcast transmitter sites and studios.
COMMERCIAL: High-rise building, elevator control, large A/C chillers,
lighting, and other sensitive critical systems.
INDUSTRIAL: Industrial automation, process control, CNC, factory robotics,
heavy load machinery.
MEDICAL: X-ray, CT scanner, MRI system, Radiation therapy machine, other
medical imaging equipments.
TELECOM: Mobile base stations, exchanges stations, control centers and
transmission relay stations, .
Single phase: 220/230/240V ±20%
Three phase: 380/400/415V ±20%
The other input voltage range and rated voltage can be custom
Single phase: 220/230/240V ±1-5%
Three phase: 380/400/415V ±1-5%
|Voltage Regulation Mode||Independent phase regulation for three phase|
|Insulation Class||H class|
|Method of Voltage Regulation||Regulation transformer with servomotor|
Single phase: 2000V/1min without puncture
Three phase: 2500V/1min without puncture
|Efficiency||>97% on full load|
|Overload Rating||Withstand 200% overload in short time|
|Protection class||IP20(indoor), outdoor type on request|
|Electrical safety||CE equivalent|
|Operational Temperature||-20 °C to +45 °C|
|Functions||Malfunction protection, Short-circuit protection, Lack of phase
protection, Wrong sequence protection, Over voltage protection,
Under voltage protection, Overload protection, Safe start, Manual
bypass, Indicating alarms.|